For the purpose of communicating some of the requirements of the Virginia Uniform Statewide Building Code (USBC) as well as some of the policies of this office, we have prepared this collection of information to be given out to you with your permit. If there are any portions which you do not fully understand, please call or come by our office. We hope this information will prove beneficial to you as your project develops toward completion.
The USBC sets out minimum inspections, which must be performed by this office. These inspections are included in the list of MANDATORY INSPECTIONS below. Generally, these are the only inspections required for single-family dwellings, however, depending on the scope of work, additional inspections may be needed.
The USBC specifies that it is the responsibility of the permit holder to assure that all required inspections are performed. All ladders, scaffolds and test equipment required to complete the inspection must be provided by the person requesting the inspection.
- If a Land Disturbing Permit (or Agreement in lieu of a plan) has been issued, construction road stabilization and erosion control perimeter measures must be installed and written verification from the responsible land disturber received prior to any inspections. Final grading must be achieved, seeding & stabilization established before occupancy approval.
- Post the Permit Card in a clearly visible location prior to requesting the first inspection.
- Final inspections must be requested, performed, and approved and a Certificate of Occupancy issued prior to occupying any part of a structure.
- No work is to be covered until an inspection has been performed and approved.
- Under normal conditions, inspections will be conducted within two working days of the time of the request.
- FOOTING: After digging is complete and bulkheads, reinforcement and grade stakes are set, but before any concrete or other material is placed (it is recommended that all vegetation & organic soils be removed at this time as it is required to be removed prior to final approval).
- CONCRETE PREPARATORY WORK: After all forms & reinforcement are installed but before any concrete is placed (poured foundation walls, etc.)
- SYSTEMS GROUNDWORK: Any systems components (including cables, piping, & duct) installed underground, under slabs or similar locations prior to covering (all drainage piping stubs must be identified).
- FOUNDATION BACK FILL: Foundation drain, damp proofing and foundation anchorage.
- ELECTRICAL: Cable & boxes installed and all joints complete including equipment grounds but before any concealing materials are placed.
- PLUMBING: DWV and distribution complete to 5 feet outside of building foundation and with test in place but before any concealing materials are installed.
- MECHANICAL: All duct work and vent piping complete but before any concealing materials are placed (equipment need not be placed).
- GAS PIPING: Piping complete to appliances shut-off valves but not connected to appliance with test in place and no concealing materials installed.
- FRAMING: After all rough ins have been approved but before any concealing materials are place
- INSULATION: After framing has been approved but before any wall or ceiling coverings are placed (blown in and exposed floor joist insulation can be inspected on final) and for slab floors of conditions spaces with an elevation at or above grade before concealing materials are placed.
- FINALS: After completion of all work represented on the approved plans, utilities have been connected and permanents vegetation established, but before any occupancy takes place.
- TEMPORARY SERVICE: Equipment set and anchored at least 1 ground rod in place and all receptacle outlets provided with GFCI protection
- EARLY SERVICE: After building is “closed in” (doors, window, & roof covering installed) any energized receptacle outlets must be GFCI protected as long as construction work is in progress.
IF WORK IS FOUND TO BE INCOMPLETE AFTER AN INSPECTION HAS BEEN REQUESTED AND SCHEDULED, A REINSPECTION FEE OF $25.00 WILL BE DUE.